Visit the Energy Systems Laboratory Homepage.
Utility Public Benefit Funds Renewed Interest at the State and Federal Levels
Texas A&M University main campus in College Station consists of 114 buildings served by two central plants. The two main campus loops are more than 50 years old with a total piping length for each loop in excess of 13 miles. The main campus has long had a problem with thermal distribution to the 114 buildings served by the central plants. Pressure problems were encountered in the chilled water and hot water distribution system during peak demand periods. The differential pressure between supply and return headers at buildings far from the central plants was negative, in the middle area was neutral, and close to the plant was positive. Various modifications were performed over the years without completely solving this problem. Discovering the real cause could help improve the thermal distribution and help determine how to best operate the system. This paper presents the causes and recommendations for the correction of the thermal distribution problems, which include not only malfunctioning automatic building hydraulic controls, but also some building hydraulic configurations themselves. Based on the findings, the thermal distribution problems will be solved by repairing the controls and retrofitting building hydraulic configurations as needed.
Verdict, M. (2006). Utility Public Benefit Funds Renewed Interest at the State and Federal Levels. Energy Systems Laboratory (http://esl.tamu.edu); Texas A&M University (http://www.tamu.edu). Available electronically from